Every standby generator requires at least one transfer switch
The Ontario Electrical Safety Code specifies that 'under no circumstances shall a generator be connected to any portion of a wiring system except where it is connected through a transfer device that makes it impossible for the generator to feed back into the normal power supply.' A transfer device is required between the utility system and the generator for safety, to prevent:
The transfer device should be sized according to the current rating of each service connected to it. It must be sized for 100% of the largest service, and 75% of the balance of services. Only a qualified electrical contractor following local electrical codes should install the transfer device.
Transfer Switch Types
The simplest and cheapest method is to use an extension cord, running only those few items you want to back up.
Generator Transfer Panel is an simple method of hooking up a generator to
your location. The generator panel receives power from your normal distribution
panel while Hydro is doing their job. When grid power fails; you start your
generator, plug it into a special plug and switch the generator panel to receive
power from the generator. The generator panel powers only those circuits you
have chosen to back up. This means you won’t need to go around turning things
off etc. The panel shown at right is a combination panel, which in some cases
will be more practical than using a separate generator panel because space is
The diagram at left shows a simple double throw switch and a small sub distribution or generator panel.
Generator Transfer Switch is another alternative. These come in two flavours, manual and automatic. A good automatic switch will do more than turn itself on. It will start the generator when it’s needed and shut it down when the power failure is over. It will also “exercise” the generator from time to time making sure it will start when it’s needed. The switch shown at right is an automatic three-phase 225A switch. (A single-phase switch looks almost the same.)
A Pole top Generator Switch is an inexpensive option frequently used by farms. This is a variant of the double throw switch but is mounted on the service pole. And yes, a long insulated pole is required to manipulate the switch.
Meter Base Generator Switches are available and are just as their name implies. They fit between the electrical service meter and the meter base. Meter base switches may be manual or automatic.
An advantage of a meter base switch is that re-wiring within the house at the frequently congested and space limited distribution panel is not required; the switch is at the meter. The generator is plugged into the bottom of the switch control
Contact Us: For Service, Parts and Help sizing your generator needs
Telephone: toll free at 1-888-810-4709
Send mail to: email@example.com with questions or comments about our product or web site.
Carribean, US, Ontario, Canada, Parry Sound, Northern Ontario,Muskoka and Georgian Bay
© Copyright 2004, All Rights Reserved - POWERTOGO™